When you choose Philips Dynalite, you are selecting the world’s finest lighting control system. Tried and tested in more than 30, projects, we have. The Philips Dynalite lighting control system has been installed and serviced in over 35, projects worldwide for over 25 years. Lightmoves has been installing . Dynalite is a lighting and automation control system developed in Sydney, Australia by a company of the same name. In the company was bought by Philips to become Philips-Dynalite.
|Published (Last):||14 September 2006|
|PDF File Size:||15.56 Mb|
|ePub File Size:||6.37 Mb|
|Price:||Free* [*Free Regsitration Required]|
Dynalite components communicate using DyNet. All of the Antumbra panels come with a range of fascia and rim colours to choose from. An OpCode of 00 to 03 means the action is to send the given area into preset 1 to 4 plus 8 times the value of Data 3 over the time specified by Data 1 and Dynalitte 2.
The ‘Message on Change’ system only sends a message every time a lighting state is to change, as opposed to the DMX protocol, which is constantly streaming the entire data-map.
Where previous versions of the Antumbra panel where physically limited to six buttons, the AntumbraDisplay can scroll through numerous virtual pages of different button configurations, making the possibilities endless. User Interfaces – Switches, panels, motion and heat sensors, touch screens and recently IOS devices. So, sending ‘Area 3 Preset 4’ will turn off the lights in Area 3 room 3.
The design opens the possibility of devices missing messages. The DyNet protocol offers no error correction or transmission control, each network message is sent on a ‘best effort’ basis. Lightmoves has been installing, servicing and programming Dynalite systems since the beginning. July Learn how and when to remove this template message. Each room is called an Area.
Lightmoves has had Antumbra panels installed philjps many projects in Victoria -including offices, healthcare facilities and residential homes. Energy Savings By using intelligent lighting systems, natural light is harvested and supplementary lighting adjusted accordingly, resulting in optimized environmental performance. In the case of a user pushing a button to turn on a light, this does not present a large problem as the user will probably notice and press the button again, but if it is an automated message say, from a timeclock, there is potential for an important message turning on outside lights of a shopping center to be missed.
The usual workaround for this is to simply send the important message twice or more.
In the company was bought by Philips to become Philips-Dynalite. These three are called Channels. For more information and Antumbra panels or lighting control solutions for your upcoming project or home please contact Lightmoves on 03 Manufacturing companies of Australia Electronics companies of Australia Lighting brands Building automation Home automation companies. Please improve this by adding secondary or tertiary sources. Each panel has its own integral temperature sensor that can be monitored and integrated with HVAC systems and light sensors to detect ambient light levels.
Sending ‘Area 3 Preset 2’ will set the lights to a low level, which is customisable.
DyNet 2 is used mainly to upload data to devices on the network. Lighting up the World with Philips Dynalite.
It allows larger messages of data to be sent at higher speeds baudsignificantly reducing lag time. The system is commonly used for lighting controlbuilding ;hilipshome automation and room automation applications and is sold worldwide.
Views Read Edit View history. You can configure and control all the lights from any point on the network. Articles lacking reliable references from July All articles lacking reliable references.
The Philips Dynalite Antumbra range. Network connectors extend the range of the network, as well as providing integration with other technologies such as AMX, Crestron, etc. This allows for much more devices on a single bus, but also leads to missed messages – as below. Dynalite is a lighting and automation control system developed in Sydney, Australia by a company of the same name. Introducing the Philips Dynalite Antumbra Display. Logical messages talk to Areas and Channels, and physical messages talk directly to the devices.
The Philips Dynalite lighting control system has been installed and serviced in over 35, projects worldwide for over 25 years. Distributed Control and Monitoring You can configure and control all the lights from any point on the network.
This is all customisable either by the programmer, or if it has been allowed, by the end user as well. The Envision editor was launched in and is designed to be more intuitive and easy to use. This means that if a transmitted message is corrupted or missed by a receiving device, there is nothing to pick up that the message was not received, but also makes for much faster communication and response to user input in ideal situations.
As most of the DyNet is openly published, it is possible to integrate with third party devices.
Dynalite – Wikipedia
The network components are all used to set a system of Areas and Channels. Based on the hugely successful AntumbraButton, the AntumbraDisplay features a central LCD display to present multiple pages of functions and system information. This article relies too much on references to primary sources. The previous Dynalite programming software dLight 2 commonly in use up toand still sometimes used for older equipment was built progressively upon a Windows 3.
In Preset 1, typically, all lights etc. From Wikipedia, the free encyclopedia. It is designed for programmers – it is not expected that end users will be able to set up their own systems, one needs training usually free provided by Dynalite distributors. Retrieved from ” https: End of line dyalite is required . Ease of Installation and Configuration The DyNet system is easier to install and takes less time to configure than conventional systems.